Waterless Co. Inc. No-Flush™ urinal Model #2004 Sonora™ Bottom Drain, wall hung, made of High Performance Composite material (HPC) for commercial or home use. Urinal to have elongated rim, a full 2” interior drain and 2” anged waste outlet; suitable for direct connection to a 2” waste at the wall . Supplied EcoTrap® insert required. Trap insert to be of a vertical ow type with 360 degree perimeter openings and installed by press t. Trap must be replaceable and rellable. Trap inserts are to be removed with a two pronged heavy duty stainless steel tool. Urinal to be fastened at the bottom front using standard bolts from brass urinal ange. The bottom of the urinal is to be fully enclosed.
CODES/STANDARDS APPLICABLE: Complies with A117, ASME A112.19.19, others.
FOR STANDARD INSTALLATION: mount at 24” above finished floor to lip of urinal or as required by architect. Center drain line to be at 15.25” off finished floor.
FOR ADA REQUIREMENTS: mount at 17“ above finished floor to lip of urinal. ADA center drain line to be at 8.25” off finished floor.
Supply suitable wall support, i.e. carrier. Install and maintain as per manufacturer’s instructions.
Urinal 2” drain outlet installs and drains to 2” anged waste. Retrot or new construction. Use standard sanitation practices to maintain xture.
Urinal is predrilled to accept most 2” brass anges from other manufacturer’s urinals in a retrot scenario. For new construction, specify #5001 brass urinal ange for 2” waste. On site custodial training is to be provided by the manufacturer or their representative. Certicates of training are to be issued and forwarded to the owner.